OSCILLATING (High Elevation) PORTABLE ATTACK MONITOR BLITZFIRE
OSCILLATING (High Elevation) PORTABLE ATTACK MONITOR
The Portable Monitor shall be Light weight, High Elevation, self-oscillation having a maximum flow rating of 500 GPM to be supplied. The Mechanism shall allow the nozzle to automatically sweep 10, 15 or 20 degrees left and right of center without having any water contact with Gears or Oscillation mechanism. The Portable Monitor shall have a disconnect feature to allow for manual horizontal rotation.
The monitor shall include an integral safety shut off valve that will automatically shut down the water flow in the event control of the monitor is lost. The water flow of Monitor shall be controlled by a six position detent, turbulence free slide valve. The detent flow control shall also function as the reset for the safety shut off valve to resume water flow.
The water inlet shall pivot up and down to allow for stability on uneven surfaces. The discharge has vertical elevation travel between 10 and 86 degrees above horizontal with a ball and socket joint. The same ball and socket joint shall allow for horizontal adjustment of 20 degrees left and right of center.
The monitor shall have folding stabilization legs with carbide tips, which are concealed in the carry and stow positions. An integral carrying handle that also functions as an attachment point for the included anchor strap shall be provided. For corrosion resistance, the monitor shall be constructed from hardcoat anodized aluminum alloy and have a blue/red powder coat interior and exterior finish.
Nozzle shall be supplied with dual pressure automatic nozzle which shall have an adjustment for pressure rating of 100 or 55 PSI and a flow range of 100-500 GPM.The nozzle design shall allow for straight stream through dense wide fog patterns and be able to be flushed without shutting down. The ribbed rubber bumper shall allow for stream shape adjustment. For corrosion resistance and durability, the nozzle shall be constructed from hardcoat anodized aluminum alloy, a protective rubber bumper with fog teeth, laser engraved serial number, reflective labeling and five year warranty. The nozzle shall comply with the current NFPA 1964 standard. The nozzle shall have a female swivel rocker lug coupling inlet and male rigid outlet.
Monitor shall be supplied with storage bracket and mounting screw. The bracket shall be constructed from stainless steel and hardcoat aluminum and be designed for horizontal or vertical installation. The bracket shall include an adjustable strap assembly for elimination of nozzle movement.